Lockwood Padde Series DE6SC Delayed Egress Device Lockwood Padde Series DE6SC Delayed Egress Device Lockwood Padde Series DE6SC Delayed Egress Device The DE6SC is designed to alert a user if an unauthorised attempt is made to access a door, particularly when free egress is required. The unit emits an infrared beam down towards a panic bar or lever. A small piece of reflective tape is placed on either of these two devices and when an attempt is made to push the panic bar or lever, the DE6SC will trigger an alarm. After 15 seconds the DE6SC releases the electronic locking mechanism thereby unlocking the door. The alarm continues to sound giving someone the opportunity to investigate the security breach. The unit is reset by disconnecting the power, this can be achieved through a keyswitch or access control panel. The delayed exit operation of the DE6SC will be overridden in the event of a fire alarm or duress. The ability to override the delay is what makes the DE6SC suitable for the locking of fire door or general emergency exits. Key Features Slave lock input for double doors Fail safe push to exit input Alarm output connected directly to siren Remote monitor alarm output Lock Monitoring Door Monitoring Applications Fire exit doors for retail or commercial environments Standards and Compliance CE Approved C-Tick Certified Successfully fire rated up to 2hrs on fire door assemblies in accordance with AS1905.1. 2005 (Part 1: Fire resistant door sets) Locking Mechanism (ES6000) conforms with the relevant requirements in accordance to AS4145.2 Conforms to D2.21 of the BCA (Building Code of Australia) Specification Voltage12v AC or DC Current12Vdc -375ma after 1 second (830ma Initial draw) MonitoringLock and Door monitoring Holding Force1500lbs 680kg Pre-load660lbs 300kg Enviroment Operational Temperature range -20 deg - +60 deg Specification StatementThe Delayed Egress System must be "Deemed to satisfy" the relevant sections of the Building Code of Australia. The system should be capable of integration with the building fire system where activation of the fire system will directly and immediately release the lock.An audible alarm should indicate to a person wishing to exit that a delay before door release is active and a distinctive change of this audible alarm would indicate the door is available for immediate exit. The delaying circuits should also be suitable for instant by-pass if an emergency pushbutton is fitted adjacent to the door.Full monitoring of lock status and door position should be available from within the system. Resetting of a released door should be by a local key re-set or remotely re-settable depending on site requirements. Close Downloads Electromechanical Door Solutions.pdf (.pdf, 8.4 MB) Close Part numbers Trade Pack Description Part Number DE6SC Delayed Egress White Hook Lock 100610-050 DE6SC Delayed Egress Black Hook Lock 100610-030 DE6SC Reflective Tape 220600-507 Close Where to buy? Find your local Lockwood stockist. Lockwood 9000/9100 Series Electromechanical Rim Type Panic Exit DeviceSuitable for single and double door applications. Lockwood 9300/9400 Series Electromechanical Vertical Type Panic Exit DeviceSuitable for single and double door applications. Lockwood 8002 Series Swing Door OperatorOpens with motor and closes with spring.